plug socket timer switch,touch sensor lamp switch
two way control switch, plug socket timer switch,in Home & Garden, Building Materials & DIY, Electrical,
Tips on how to Wire 3 Way Light Switch
Romex 12-2 or 14-2 for the feed wire.
Note: Romex 12-3 or 14-3 wire has 4 conductors in it, three are sheathed (white/black/red) and one is bare copper (ground). Romex 12-2 or 14-2 wire has 3 conductors in it, two are sheathed (black and white) and one is bare copper.
Always use the identical gauge of wire for the whole circuit, either 14-x or 12-x gauge.
– Two SPDT (single pole double throw) switches
– Wire Nuts
plug socket timer switch – Copper crimp tubes
Working with electricity may be life threatening. Consequently, when installing a 3 way light switch ensure you first turn power off to the feed line that may power the three way light switch. The feed line ought to be turned off on the circuit panel.
Instructions for Installing 3 way Light Switch
Step 1: Run a feed cable to the primary light switch from the underside of the switch box. This is effectively the facility feed coming from the circuit panel.
Step 2: Run another cable, known as the traveler between the first switch and the sunshine fixture.
Step 3: Run another traveler cable from the sunshine fixture to the second switch.
Step 4: A 3 way switch has a common terminal at the bottom and two traveler terminals at the highest. Consequently it is wise to have the traveler cables are available in from the highest of the switch boxes.
Step 5: At the first 3 way switch box, wire the black feed line to the common terminal which is on the bottom right.
Step 7: Next wire the red traveler wire (again a “hot” wire) to the left traveler terminal.
Step 8: At the first switch box, attach the 12-3 white wire “neutral wire” to the 12-2 feed neutral wire with wire nuts.
Step 9: Again, at the first switch box, connect the bare copper ground wires together using lineman’s pliers. Twist the copper wires together several times and add a copper crimp tube over them.
Step 10: At the light box, again connect the bare copper ground wires together using lineman’s pliers. Twist the copper wires together several times and add a copper crimp tube over them.
Step 11: At the plug socket timer switch light box, connect the red wires along with a wire nut.
Step 12: Again, at the sunshine box connect together with a wire nut the black wire coming from the primary 3 way switch box, and the white wire coming from the second 3 way switch box. Since you’re connecting a black “hot” wire to a white wire that is typically neutral it is important to mark this white wire as now “hot”. To do this, attach a piece of black electrical tape on each end of the white wire that you just connected to the black wire.
Step 13: On the second 3 way light switch attach the white wire (with the black tape on it indicating it is now used as a “hot” wire) to the highest right traveler terminal.
Step 14: At the second 3 way light switch attach the red wire to the highest left traveler terminal.
Step 15: Again on the second 3 way light switch, connect the black wire to the lower right common terminal.
Step 16: Again on the second 3 way light switch, connect together the bare copper ground wires. Twist the copper wires together several times and add a copper crimp tube over them.
Step 17: With the circuit wired up you need to be left with at the sunshine box a white wire end (neutral wire) that comes from the first switch box, a black wire (hot wire” that comes from the second switch box, and a bare copper ground wire (associated with the twisted copper wires coming into the light box from the two Romex cables.). These three wires then connect to the light fixture. The ground wire connects to the sunshine chassis, and the black wire end to one in every of the sunshine fixture terminals, and the white wire end to the other light fixture terminal. After you have wired the sunshine fixture attach it to the sunshine box.
Step 18: Secure the 3 way switches into their switch boxes and attach face covers.
Step 19: Power up the switch circuit, back at the circuit breaker panel box. Next, test the sunshine. If you happen to followed these instructions perfectly you must have a properly working 3 way light switch.
plug socket timer switch